Separate names with a comma.
Discussion in 'Garages, Workshops & Tools' started by clay's70, Jan 25, 2015.
So it's a 240v
That's a 3 phase contactor and you're using single phase. You can get a single phase contactor and maybe save a few bucks.
If there's a neutral with the 240V circuit, you can use a 120V coil, or if not stick w/ 240v.
Got the new one a couple of days ago. I was able to get it thru work
so I saved a bunch. Now to find some time to put it in.